Protocols: SNMP and DCPx
Discrete Inputs: 32 (expandable to 176)
Alarm Detection Speed: User-defined (3 to 999 msec)
Analog Inputs: 8
Analog Input Range: (-94 to 94 VDC or 4 to 20 mA)
Control Outputs: 8 Form C relay contacts
Maximum Voltage: 60 VDC/120 VAC
Maximum Current:1 Amp, AC/DC
IP Address Ping Targets: 32
Modem: 33.6K internal
Visual Interface:LCD display with descriptive text 6 bicolor LEDs
Audible Interface: Alarm speaker
Dimensions: 1.75"H x 17"W x 12"D, (4.5 cm x 43.2 cm x 30.5 cm)
Mounting: 19" or 23" rack
Power Input: -48VDC (--40 to -56 VDC) see options
Current Draw: 200mA
Fuse: 1 Amp GMT
Operating Temperature: 32°-140° F (0°-60° C)
Operating Humidity: 0%-95% noncondensing
A Lightweight, Compact Test Box for Your RTUs
If an alarm point fails, it's important to know if the problem lies with your NetGuardian, your site equipment, or your analog sensor. With the NetGuardian Test Box, minimize windshield time driving to remote sites by diagnosing problem while you're on-site.
The labeled toggles and knobs on the NetGuardian Test Box are easier than working with probes directly on amphenol connectors. With a Test Box, you can easily set all of the alarms you want.
You need to see DPS gear in action. Get a live demo with our engineers.
Download our free Monitoring Fundamentals Tutorial.
An introduction to Monitoring Fundamentals strictly from the perspective of telecom network alarm management.
Have a specific question? Ask our team of expert engineers and get a specific answer!
Sign up for the next DPS Factory Training!
Whether you're new to our equipment or you've used it for years, DPS factory training is the best way to get more from your monitoring.Reserve Your Seat Today