You need to see DPS gear in action. Get a live demo with our engineers.
Have a specific question? Ask our team of expert engineers and get a specific answer!
Sign up for the next DPS Factory Training!
Whether you're new to our equipment or you've used it for years, DPS factory training is the best way to get more from your monitoring.Reserve Your Seat Today
The AlphaMax 82S is a compact dial-up alarm system remote. The 82S is generally used with equipment such as radio equipment where you have discrete alarms and a serial provisioning port. The 82S would notifiy you via pager about the problem. You can then dial in using the same phone facility to reach through and provision or correct the problem.
Alarms can be communicated to an alphanumeric or numeric pager or they can be forwarded to a monitoring center equipped with an alarm management system. Because the AlphaMax is configured by downloading from a remote PC, maintenance and upgrades become routine.
Configuring AlphaMax is easy using T/Alpha software for Windows. T/Alpha will also monitor alarm inputs and operate control relays.
AlphaMax's optoisolated alarm inputs are normally in the "active state" when grounded (current flowing). Alarm points can be individually "reversed" by remote programming to assume the Active State when ungrounded (no current flowing). Each alarm input can be configured for unipolar operation (reports going to alarm state only) or bipolar operation (reports both going to alarm state and returning to cleared state).
Each point can also have a 30 character description (ex: "Room Too Hot!"), a qualification time period before dialing primary and backup pager numbers. A redial option causes the unit to dial a pager up to 15 times in case of no answer.
Personnel with pagers can call into the AlphaMax from a dial tone (DTMF) phone and acknowledge alarms, operate control points and request a status report.
In addition to being activated remotely, control relays may be activated internally by a combination of existing alarms, based on a programmable equation (derived control). Each control point may have up to two equations defined.
The AlphaMax uses an internal 300/1200 baud "AT 212" type modem. The control relay outputs are Form "C". A high speed version that has a 33.6K modem is also available (see ordering options).
Want more information?